APPLIANCE GAS CONNECTION
IMPORTANT: This appliance must be
WARNING: DO NOT MODIFY THIS
If the appliance cannot be adjusted to perform correctly, contact the service department.
This appliance utilises a threaded 1/2" gas male fitting.
To connect the appliance to the gas network with a flexible hose, a supplemental hose nipple fitting is needed which is supplied
with the appliance. (Fig. 05).
leg heights –
Gas inlet (mm) - Nat gas Gas inlet (mm) -
From RH rear side: 35 mm From RH rear side: 35mm
Up from floor: 560 - 595mm (590mm nominal) Up from floor: 645 – 680mm (675 mm nominal)
The gas connection is via 1/2" tapered thread. Connect the cooker to the gas supply and test for leaks. NEVER use a naked
flame to check for gas
Natural Gas: Gas regulator supplied with the appliance must be installed.
LPG: Test point adaptor to be fitted and checked at time of installation.
Using a flexible connection
This appliance is approved for connection with a flexible hose, which complies with the AS/NZS 1869 (AGA Approved),
10mm ID, class B or D, between 1-1.2m long.
Connection shall be in compliance with AS5601.
When installing the hose restraint device, the appliance anchor point is the rear panel.
Using a Copper Pipe
The cooker must be connected to the gas supply with upstream connection of an isolation valve in accordance with the respectively
valid regulations. We recommend that the isolation valve be fitted prior to the cooker to enable isolation of the cooker from the
gas supply. The valve must be easily accessible at all times.
To find out the gas type factory settings, see label on the rear of the appliance.