6 - 13
6. SET MODE
The display which appears will allow you to enter the alarm
Set the alarm value using the  and  keys. After
setting, press the [ENT] key.
The decimal point is predetermined by the input range.
Relationship between Input Range and Decimal Points
Type of Input
Position of Decimal Point
–20.00 to 20.00 mV
–60.00 to 60.00 mV
–200.0 to 200.0 mV
–2.000 to 2.000 V
–6.000 to 6.000 V
–20.00 to 20.00 V
The following settings are available only for the model with
relay options (A2/A4/A6). For models without these options,
the alarm setting ends by pressing the [ENT] key until
Determines whether the relay outputs a signal or not when an
Select ON/OFF by the  key, and press the [ENT] key.
Sets the number of the relay after the alarm output ON is
selected. A numeric to be set is selected from I01 to I06 by the
 key. Then press the [ENT] key.
NOTE If a number larger than the available number of output relays is selected, the
alarm output will not implemented.
 is displayed and the setting is completed. Press
the [ENT] key to set another channel; or press the [DISP]
key for three seconds to return to the OPERATION mode.
NOTE •As a merged function, a combination of remote control option (- R) and alarm
output relay option is available to change the chart speed when an alarm
•If you press the [ESC] key in the middle of setting, the indication returns to
the  and already set data will be aborted.
6.3 Setting Alarms (ALARM)