Refer to Figure 2-1, outline and installation drawings. Drill
mounting holes where appropriate.
Refer to Figure 2-2, wiring the FLSC-28 for the appropriate
terminals for interconnections.
The signal leads f rom the turbine should be shielded whenever
the FLSC-28 is not integrally mounted. Ground shield on one
end only If desired, use solder lug provided on ground stud.
Connections to the terminal block should be carefully dressed to
avoid having bare wires extending pass the screw clamp on the
terminal block. This is particularly important for units mounted
within the explosion proof enclosure. Wires should be neatly
dressed near bottom of enclosure to assure wiring will not
become fouled when cover is installed.
Figure 2-1. Intallation Dimensions