– 46 –
SUMMARY OF AUDIBLE NOTIFICATIONS
(FIXED-WORD DISPLAY KEYPADS)
SOUND CAUSE DISPLAY
LOUD “BEEPING” (keypads)
Temporal pulsed sound from
external sounder* & keypad(s)
FIRE ALARM FIRE & ALARM is displayed; zone number of zone in alarm is displayed.
Keypad & External
ALARM is displayed; zone number of zone in alarm is also displayed.
ONE SHORT BEEP
a. SYSTEM DISARM
b. SYSTEM ARMING ATTEMPT
WITH AN OPEN ZONE.
c. BYPASS VERIFY
a. READY is displayed.
b. The number of the open protection zone is displayed.
c. Zone numbers of the bypassed protection zones are displayed (one beep is
heard for each zone displayed). Subsequently, the following is displayed:
BYPASS and READY
ONE SHORT BEEP
(once every 15 seconds)
SYSTEM IS IN TEST MODE Opened zone numbers will appear.
ONE BEEP every 40 sec.
LOW BATTERY AT A TRANSMITTER BAT displayed with zone number of transmitter.
TWO SHORT BEEPS
ARM AWAY OR MAXIMUM AWAY or AWAY & INSTANT is displayed. Red ARMED indicator is lit.
THREE SHORT BEEPS
a. ARM STAY OR INSTANT
b. ZONE OPENED WHILE SYSTEM
IS IN CHIME MODE.
a. STAY or INSTANT is displayed. Red ARMED indicator is lit.
b. CHIME displayed; zone number of open protection zone will be displayed if the
[*] key is pressed.
b. MEMORY OF ALARM
a. CHECK displayed. Zone number of troubled protection zone is displayed.
b. FIRE or ALARM is displayed; zone number of zone in alarm is displayed.
a. EXIT DELAY WARNING (if
b. ENTRY DELAY WARNING
a. AWAY or AWAY & INSTANT is displayed.
b. Exceeding the entry delay time without disarming causes alarm.
* If bell is used as external sounder, fire alarm is temporal pulsed ring; burglary/audible emergency is steady ring.
** Entry warning may consist of three short beeps or slow continuous beeping, as programmed by your installer.
*** Loss of system battery power is not indicated or annunciated by the keypad (warnings are for loss of AC power only).