20 | P a g e
TIMBER FRAME INSTALLATION
Frame out Dimensions (in mm)
* Indication only. Can be smaller or larger.
1. At frame stage the builder shall provide a 10amp GPO to the rear back corner of the frame out with an
isolation switch fitted at the appliance or on an adjacent wall within the room where the
fire can be seen. An adequate gas line should be run down the front right hand side of the
frame out terminating approximately 1m from the base, this should be run down the inside face
of the timber.