A. Air Intake Diffusers Ducts - Assembly and Installation
i) Install the decorative plate by pressing on
both sides of the plate.
B. Hot Air Diffusers Ducts
Ducts for the hot air diffusers must be 200 mm in diameter, flexible or rigid (rigid is highly
recommended), insulated or not, with a 25 mm clearance to heat sensitive materials. Total length
of duct must not exceed 4 meters. Hot air diffusers must have a 152 mm clearance to heat
sensitive materials. Hot air diffuser’s framing should be 318 mm X 295 mm.