INSTALLATION INSTRUCTIONS (continued)
EXTERNAL WALL MOUNTED FAN MODULE INSTALLATION
1. Wall mounted fan module – terminal must be installed with clearances as specified by
AS5601.1 Clause 6.9.3
2. Run exhaust flue and air intake flue as required – Maximum run 3m. Flues can be run next
to each other. Maintain clearances to combustibles.
3. Connection to appliance
Recommended Silicon – Non-acetic, neutral cure
150°C or higher temperature rated.
Bostik RTV 926 or similar.
Apply an 8mm thick silicon bead fully around heater
connection approx. 10mm from the top.
Cut tube to length where required.
Ensure ends are burr free and round, test fit flue will
slide over connection.