INSTALLATION INSTRUCTIONS (continued)
0M-5M FLUE – INLINE FAN MODULE WITH WALL TERMINATION
Setup with internal fan module with wall termination – mid flue mounted
Maximum 5m flue length
1. Wall terminal must be installed with clearances as specified by AS5601.1-2013 Clause 6.9.3
2. Run exhaust flue and air intake flue as required – Maximum total run 3m per flue. Flues can
be run next to each other. Maintain clearances to combustibles.
3. Mount fan controller in the required location. (Access to the fan module is required for
servicing, if the fan module is located inside a boxed frame, allow a 450 x 450 access
4. Connection to fan module to appliance
Run flue from appliance to bottom entry on fan module. Support flue with brackets as required.