INSTALLATION INSTRUCTIONS (continued)
Locate terminal on wall and predrill mounting holes
Cut flue exhaust tube (hot tube) to length (Flue must
extend a minimum of 50mm past the exit face of
wall.) It is recommended that the tubes are cut
slightly longer and pushed back into wall upon fixing
of wall terminal. Allow flue movement between
terminal and last flue hanging clip.
Cut Air intake as per flue exhaust.
Ensure ends are burr free and round, test fit flue will
slide inside both the hot exhaust connection and air
Feed air hot exhaust flue into connection, ensure
inserted 50mm. Fit retaining screw from below.
Feed air intake flue into connection, ensure inserted
50mm. Fit retaining screw from below.